HVAC Specialists Serving those in West Carrollton, Ohio 45342, 45439, 45449, 45459
The city of West Carrollton has a population of over 12,000 and is home to more than 200 companies. It is located in Montgomery County and is 8 miles southwest of the city of Dayton. West Carrollton has over 100 acres of parklands, affordable homes, a public swimming pool, a soccer complex, and more that makes it a notable suburb of Dayton. We here at Kettering-Oakwood Heating & Air are honored to provide our services to the citizens of West Carrollton.
Kettering-Oakwood Heating & Air is proud to serve the community of West Carrollton. Call 937-502-3842 to talk to one of our customer service representatives or schedule online here with our simple online form. We’re here to help you!
for West Carrollton, OH
I completed a diagnostic service call on an air conditioner. I found the AC to be receiving no power. I then found terminals at the compressor shorted to the ground, popping the circuit breaker. Finally, I provided and went over options with the customer.
I performed a diagnostic on clients system that was not producing any cool air. Low cool caused by no maintenance. Dirty indoor coil, dirty outdoor coil, low blower cap and no roof access.
I completed a diagnostic call on a approximately 40 to 50 year old furnace that is not working. The pilot is not lit. I took off the cover to access the burner and pilot area and found that this furnace is in very poor condition, heat exchanger is completely rusting out, evidence of flame rollout near the right side of the burner enclosure. I cleaned thermocouple and relit pilot and it stayed lit. Furnace is working on my departure but I told customer due to the age and the condition I cannot give him any guarantees he won’t have further issues. If the pilot continues going out it is probably being blown out. Provided customer with estimate on a replacement furnace.
I completed a cooling repair for an inducer motor.
I completed a diagnostic service call upon arrival I Replaced a new inducer motor customers moving and not interested in the furnace upgrade we are trying to source the part and hopefully do the repair today before the weekend. Customer has no heat at this time.