HVAC Specialists Serving those in Englewood, Ohio 45315, 45322, 45415
The city of Englewood is part of Montgomery County and has over 14,000 people residing in the area. The town is located 14-mile northwest of Dayton, Ohio and has various open green land and parks offered to the community. At one-point, Englewood was voted best overall community in the Dayton-Springfield metro area. We here at Kettering-Oakwood Heating & Air are honored to provide our services to the residents of Englewood.
Kettering-Oakwood Heating & Air is proud to serve the community of Englewood. Call 937-502-3842 to talk to one of our customer service representatives or schedule online here with our simple online form. We’re here to help you!
for Englewood, OH
I completed a diagnostic on an A/C. I found a loose wire on capacitor. I hosed off A/C as well. Customer wants a new system next year but for now they just wanted to diagnose the issue.
I went over the general operation of the new thermostat with customer to make sure she understood how to use it. Her system checked out good and is operating properly at this time.
Diagnostic on an Attic A/C Unit. Found unit to be low on Freon. Quoted customer price per pound. Per customers request moved forward with charging unit. All other systems components are within manufactured range. System is operating properly upon departure.
I completed the spring tune up on a Nordyne air conditioner. I visually inspected the furnace. I found that there was a wiring issue as the air conditioner would not turn on with the thermostat. After repairing wiring I found a weakened capacitor and condensation issue, I went over options w/ customer. I Checked voltage and amps. I inspected the evaporator coil. I checked the temperature difference across the coil. Checked refrigerant charge, voltages and amps. I rinsed the condenser coils with water. Cycled and monitored the system. Operating at this time.
Performed a sma tune-up and safety check-up for a AC unit. Customer stated no issues and unit has been running fine. They just moved in last year and wanted to get it checked out. Found condenser capacitor to be weak. Replaced capacitor and unit is running great. System was running upon departure.